
# KNX Binding

The openHAB KNX binding allows to connect to [KNX Home Automation](https://www.knx.org/) installations.
Switching lights on and off, activating your roller shutters, or changing room temperatures are only some examples.

To access your KNX bus, you either need a gateway device which is connected to the KNX bus and allows computers to access the bus communication.
This can be either an Ethernet (as a Router or a Tunnel type) or a serial gateway.
The KNX binding then can communicate directly with this gateway.
Alternatively, a PC running [KNXD](https://github.com/knxd/knxd) (free open source component software) can be put in between which then acts as a broker allowing multiple client to connect to the same gateway.
Since the protocol is identical, the KNX binding can also communicate with it transparently.

## Supported Things

The KNX binding supports two types of bridges, and one type of things to access the KNX bus.
There is an *ip* bridge to connect to KNX IP Gateways, and a *serial* bridge for connection over a serial port to a host-attached gateway.

## Binding Configuration

The binding itself does not require any special configuration.

## Bridges

The following two bridge types are supported. Bridges don't have channels on their own.

### IP Gateway

The IP Gateway is the most commonly used way to connect to the KNX bus. At its base, the *ip* bridge accepts the following configuration parameters:

| Name                | Required     | Description                                                                                                  | Default value                                        |
|---------------------|--------------|--------------------------------------------------------------------------------------------------------------|------------------------------------------------------|
| type                | Yes          | The IP connection type for connecting to the KNX bus (`TUNNEL` or `ROUTER`)                                  | -                                                    |
| ipAddress           | for `TUNNEL` | Network address of the KNX/IP gateway. If type `ROUTER` is set, the IPv4 Multicast Address can be set.       | for `TUNNEL`: \<nothing\>, for `ROUTER`: 224.0.23.12 |
| portNumber          | for `TUNNEL` | Port number of the KNX/IP gateway                                                                            | 3671                                                 |
| localIp             | No           | Network address of the local host to be used to set up the connection to the KNX/IP gateway                  | the system-wide configured primary interface address |
| localSourceAddr     | No           | The (virtual) individual address for identification of this KNX/IP gateway within the KNX bus <br/><br/>Note: Use a free address, not the one of the interface. Or leave it at `0.0.0` and let openHAB decide which address to use.                | 0.0.0                                                |
| useNAT              | No           | Whether there is network address translation between the server and the gateway                              | false                                                |
| readingPause        | No           | Time in milliseconds of how long should be paused between two read requests to the bus during initialization | 50                                                   |
| responseTimeout     | No           | Timeout in seconds to wait for a response from the KNX bus                                                   | 10                                                   |
| readRetriesLimit    | No           | Limits the read retries while initialization from the KNX bus                                                | 3                                                    |
| autoReconnectPeriod | No           | Seconds between connect retries when KNX link has been lost (0 means never).                                 | 0                                                    |


### Serial Gateway

The *serial* bridge accepts the following configuration parameters:

| Name                | Required | Description                                                                                                  | Default value |
|---------------------|----------|--------------------------------------------------------------------------------------------------------------|---------------|
| serialPort          | Y        | The serial port to use for connecting to the KNX bus                                                         | -             |
| readingPause        | N        | Time in milliseconds of how long should be paused between two read requests to the bus during initialization | 50            |
| responseTimeout     | N        | Timeout in seconds to wait for a response from the KNX bus                                                   | 10            |
| readRetriesLimit    | N        | Limits the read retries while initialization from the KNX bus                                                | 3             |
| autoReconnectPeriod | N        | Seconds between connect retries when KNX link has been lost, 0 means never retry                             | 0             |
| useCemi             | N        | Use newer CEMI message format, useful for newer devices like KNX RF sticks, kBerry, etc.                     | false         |

## Things

### *device* Things

*basic* Things are wrappers around arbitrary group addresses on the KNX bus.
They have no specific function in the KNX binding, except that if the *address* is defined, the binding will actively poll the Individual Address on the KNX bus to detect that the KNX actuator is reachable.
Under normal real-world circumstances, either all devices on a bus are reachable, or the entire bus is down.
When *fetch* is set to true, the binding will read-out the memory of the KNX actuator in order to detect configuration data and so forth.
This is however an experimental feature, very prone to the actual on the KNX bus.

| Name         | Required | Description                                                                                                              | Default value                                                               |
|--------------|----------|--------------------------------------------------------------------------------------------------------------------------|-----------------------------------------------------------------------------|
| address      | N        | The individual device address (in 0.0.0 notation)                                                                        | -  |
| fetch        | N        | Read out the device parameters and address/communication object tables (requires the address)                            | false                                                                       |
| pingInterval | N        | Interval (in seconds) to contact the device and set the thing status based on the result (requires the address)          | 600                                                                         |
| readInterval | N        | Interval (in seconds) to actively request reading of values from the bus (0 if they should only be read once at startup) | 0                                                                           |

Different kinds of channels are defined and can be used to group together Group Addresses.
All channel types share two configuration parameters: *read*, an optional parameter to indicate if the 'readable' group addresses of that Channel should be read at startup (default: false), and *interval*, an optional parameter that defines an interval between attempts to read the status group address on the bus, in seconds.
When defined and set to 0, the interval is ignored (default: 0)

#### Standard Channel Types

Standard channels are used most of the time.
They are used in the common case where the physical state is owned by a device within the KNX bus, e.g. by a switch actuator who "knows" whether the light is turned on or off, or by a temperature sensor which reports the room temperature regularly.

Note: After changing the DPT of already existing Channels, openHAB needs to be restarted for the changes to become effective.

##### Channel Type "switch"

| Parameter | Description                         | Default DPT |
|-----------|-------------------------------------|-------------|
| ga        | Group address for the binary switch | 1.001       |


##### Channel Type "dimmer"

| Parameter        | Description                            | Default DPT |
|------------------|----------------------------------------|-------------|
| switch           | Group address for the binary switch    | 1.001       |
| position         | Group address of the absolute position | 5.001       |
| increaseDecrease | Group address for relative movement    | 3.007       |

##### Channel Type "rollershutter"

| Parameter | Description                             | Default DPT |
|-----------|-----------------------------------------|-------------|
| upDown    | Group address for relative movement     | 1.008       |
| stopMove  | Group address for stopping              | 1.010       |
| position  | Group address for the absolute position | 5.001       |

##### Channel Type "contact"

| Parameter | Description   | Default DPT |
|-----------|---------------|-------------|
| ga        | Group address | 1.009       |

##### Channel Type "number"

| Parameter | Description   | Default DPT |
|-----------|---------------|-------------|
| ga        | Group address | 9.001       |


Note: Using the Units Of Measurement feature of openHAB (Quantitytype) requires that the DPT value is set correctly.
Automatic type conversion will be applied if required.

##### Channel Type "string"

| Parameter | Description   | Default DPT |
|-----------|---------------|-------------|
| ga        | Group address | 16.001      |

##### Channel Type "datetime"

| Parameter | Description   | Default DPT |
|-----------|---------------|-------------|
| ga        | Group address | 19.001      |


#### Control Channel Types

In contrast to the standard channels above, the control channel types are used for cases where the KNX bus does not own the physical state of a device.
This could for example be the case if a lamp from another binding should be controlled by a KNX wall switch.
If from the KNX bus a `GroupValueRead` telegram is sent to a *-control Channel, the bridge responds with a `GroupValueResponse` telegram to the KNX bus.

##### Channel Type "switch-control"

| Parameter | Description                         | Default DPT |
|-----------|-------------------------------------|-------------|
| ga        | Group address for the binary switch | 1.001       |


##### Channel Type "dimmer-control"

| Parameter        | Description                                                                                                                                   | Default DPT |
|------------------|-----------------------------------------------------------------------------------------------------------------------------------------------|-------------|
| switch           | Group address for the binary switch                                                                                                           | 1.001       |
| position         | Group address of the absolute position                                                                                                        | 5.001       |
| increaseDecrease | Group address for relative movement                                                                                                           | 3.007       |
| frequency        | Increase/Decrease frequency in milliseconds in case the binding should handle that (0 if the KNX device sends the commands repeatedly itself) | 0           |

##### Channel Type "rollershutter-control"

| Parameter | Description                             | Default DPT |
|-----------|-----------------------------------------|-------------|
| upDown    | Group address for relative movement     | 1.008       |
| stopMove  | Group address for stopping              | 1.010       |
| position  | Group address for the absolute position | 5.001       |

##### Channel Type "contact-control"

| Parameter | Description   | Default DPT |
|-----------|---------------|-------------|
| ga        | Group address | 1.009       |

##### Channel Type "number-control"

| Parameter | Description   | Default DPT |
|-----------|---------------|-------------|
| ga        | Group address | 9.001       |

##### Channel Type "string-control"

| Parameter | Description   | Default DPT |
|-----------|---------------|-------------|
| ga        | Group address | 16.001      |

##### Channel Type "datetime-control"

| Parameter | Description   | Default DPT |
|-----------|---------------|-------------|
| ga        | Group address | 19.001      |

#### Group Address Notation

```
<config>="[<dpt>:][<]<mainGA>[[+[<]<listeningGA>][+[<]<listeningGA>..]]"
```

where parts in brackets `[]` denote optional information.

The optional `<` sign tells whether the group address of the datapoint accepts read requests on the KNX bus (it does, if the sign is there).
With `*-control` channels, the state is not owned by any device on the KNX bus, therefore no read requests will be sent by the binding, i.e. `<` signs will be ignored for them.

Each configuration parameter has a `mainGA` where commands are written to and optionally several `listeningGA`s.

The `dpt` element is optional. If omitted, the corresponding default value will be used (see the channel descriptions above).


## Examples

The following two templates are sufficient for almost all purposes.
Only add parameters to the Bridge and Thing configuration if you know exactly what functionality it is needed for.

### Type ROUTER mode configuration Template

knx.things:

```xtend
Bridge knx:ip:bridge [
    type="ROUTER",
    autoReconnectPeriod=60 //optional, do not set <30 sec.
] {
    Thing device knx_device "knx_device_name" @ "knx_device_group" [
        //readInterval=3600 //optional, only used if reading values are present
    ] {
        //Items configurations
    }
}
```

### Type TUNNEL mode configuration Template

knx.things:

```xtend
Bridge knx:ip:bridge [
    type="TUNNEL",
    ipAddress="192.168.0.111",
    autoReconnectPeriod=60 //optional, do not set <30 sec.
] {
    Thing device knx_device "knx_device_name" @ "knx_device_group" [
        //readInterval=3600 //optional, only used if reading values are present
    ] {
        //Items configurations
    }
}
```

### Full Example

```xtend
//TUNNEL
Bridge knx:ip:bridge [
    type="TUNNEL",
    ipAddress="192.168.0.10",
    portNumber=3671,
    localIp="192.168.0.11",
    readingPause=50,
    responseTimeout=10,
    readRetriesLimit=3,
    autoReconnectPeriod=60,
    localSourceAddr="0.0.0"
] {
    Thing device generic [
        address="1.2.3",
        fetch=true,
        pingInterval=300,
        readInterval=3600
    ] {
        Type switch        : demoSwitch        "Light"       [ ga="3/0/4+<3/0/5" ]
        Type rollershutter : demoRollershutter "Shade"       [ upDown="4/3/50+4/3/51", stopMove="4/3/52+4/3/53", position="4/3/54+<4/3/55" ]
        Type contact       : demoContact       "Door"        [ ga="1.019:<5/1/2" ]
        Type number        : demoTemperature   "Temperature" [ ga="9.001:<5/0/0" ]
        Type dimmer        : demoDimmer        "Dimmer"      [ switch="5/0/0", position="5/0/2+<5/0/3", increaseDecrease="5/0/4" ]
        Type string        : demoString        "Message"     [ ga="5/3/1" ]
        Type datetime      : demoDatetime      "Alarm"       [ ga="5/5/42" ]
    }
}

//ROUTER
Bridge knx:ip:bridge [
    type="ROUTER",
    ipAddress="224.0.23.12",
    portNumber=3671,
    localIp="192.168.0.11",
    readingPause=50,
    responseTimeout=10,
    readRetriesLimit=3,
    autoReconnectPeriod=60,
    localSourceAddr="0.0.0"
] {}
```

knx.items:

```xtend
Switch        demoSwitch         "Light [%s]"               <light>          { channel="knx:device:bridge:generic:demoSwitch" }
Dimmer        demoDimmer         "Dimmer [%d %%]"           <light>          { channel="knx:device:bridge:generic:demoDimmer" }
Rollershutter demoRollershutter  "Shade [%d %%]"            <rollershutter>  { channel="knx:device:bridge:generic:demoRollershutter" }
Contact       demoContact        "Front Door [%s]"          <frontdoor>      { channel="knx:device:bridge:generic:demoContact" }
Number        demoTemperature    "Temperature [%.1f °C]"    <temperature>    { channel="knx:device:bridge:generic:demoTemperature" }
String        demoString         "Message of the day [%s]"                   { channel="knx:device:bridge:generic:demoString" }
DateTime      demoDatetime       "Alarm [%1$tH:%1$tM]"                       { channel="knx:device:bridge:generic:demoDatetime" }
```

knx.sitemap:

```xtend
sitemap knx label="KNX Demo Sitemap" {
  Frame label="Demo Elements" {
    Switch item=demoSwitch
    Switch item=demoRollershutter
    Text   item=demoContact
    Text   item=demoTemperature
    Slider item=demoDimmer
    Text   item=demoString
    Text   item=demoDatetime
  }
}

```

### Control Example

control.things:

```xtend
Bridge knx:serial:bridge [
    serialPort="/dev/ttyAMA0",
    readingPause=50,
    responseTimeout=10,
    readRetriesLimit=3,
    autoReconnectPeriod=60
] {
    Thing device generic {
        Type switch-control        : controlSwitch        "Control Switch"        [ ga="3/3/10+<3/3/11" ]   // '<'  signs are allowed but will be ignored for control Channels
        Type dimmer-control        : controlDimmer        "Control Dimmer"        [ switch="3/3/50+3/3/48", position="3/3/46", increaseDecrease="3/3/49", frequency=300 ]
        Type rollershutter-control : controlRollershutter "Control Rollershutter" [ upDown="3/4/1+3/4/2", stopMove="3/4/3", position="3/4/4" ]
        Type number-control        : controlNumber        "Control Number"        [ ga="1/2/2" ]
        Type string-control        : controlString        "Control String"        [ ga="1/4/2" ]
        Type datetime-control      : controlDatetime      "Control Datetime"      [ ga="5/1/30" ]
    }
}

Bridge hue:bridge:bridge "Philips Hue Bridge" [
    ipAddress="...",
    userName="..."
] {
    Thing 0210 1 "Color Lamp" [ lightId="1" ]
}
```

knx.items:

```xtend
Switch        demoSwitch         "Light [%s]"               <light>          { channel="hue:0210:bridge:1:color", channel="knx:device:bridge:generic:controlSwitch" }
Dimmer        demoDimmer         "Dimmer [%d %%]"           <light>          { channel="hue:0210:bridge:1:color", channel="knx:device:bridge:generic:controlDimmer" }
```
